Professional 25 TPH Water Softener Plant Easy Operation
The working process of water softener, generally consists of the
following steps: cyclic backwashing, salt
absorption (regeneration), slow flushing (replacement), quick rinse
five process. All processes of different
softening water equipment are very close, just because the actual
process or different control needs, there
may be some additional procedures. Any of the sodium ion exchange
based water softening equipment is
developed based on these five processes.
The automatic softener operation program:
A. Operation (work)
Raw water in a certain pressure (0.2-0.6Mpa), flow rate, the body
cavity by the controller, into the
containers of ion exchange resin (resin cans), resin contained in
Na + and the cation in the water (Ca2 +,
magnesium 2 +, Fe2 +, etc) to exchange, which makes water of Ca2 +,
magnesium 2 + ion content meet
the established requirements, to achieve the softening of hard
After the resins are expired, the backwash is carried out from
bottom to bottom before recycling.The
purpose of reverse washing is to have two, one is through reverse
washing, make the resin layer that runs
medium pressure is loosened, favorable to the resin particle and
the regeneration liquid to make full
contact;The first is that the suspended solids and broken resins
accumulated on the surface of the resin
are discharged with anti-wash water, so that the flow resistance of
the exchanger will not become larger
C. Regenerated Salt:
The regenerated salt solution is used to restore the original
exchange capacity under certain concentration
D. Replacement (Slow Cleaning)
In the regeneration solution into after exchanger is not involved
in the regeneration of salt solution
exchange, with less than or equal to the velocity of regenerated
liquid water for cleaning (slow cleaning), in
order to make full use of the role of regenerating salt liquid and
reduce the wash load.
E. Washing (Quick Cleaning)
The aim is to remove residual waste from the resin layer and
usually clean it at normal flow rate until the
water is qualified.
F. Regeneration Tank Water Flooding
The amount of salt required to regenerate the solution once more is
injected into the regeneration tank
System Configuration Details List:
The hardness of water is mainly composed of cations: Ca2 +andMg2 +
ions.When containing raw water
hardness ions through the exchanger resin layer, the water of
calcium and magnesium ions with sodium
ions in resin in displacement, resin absorption of calcium,
magnesium ion and sodium ion in the water, so
from escaping from the exchange of water is to remove the
demineralized water hardness ions.Along with
the ongoing exchange process, resin Na + all lose their ability to
exchange, after it was put out at this point
you must use the sodium chloride solution for resin regeneration,
the resin adsorption of Ca2 +,
magnesium 2 + displacement, resin adsorption of sodium ions, again
returned to soften the exchange
|Product Name||60-100 ton softened water|
|Resin model||cation exchange resin|
|Installation requirements||foundation level|
Shijiazhuang Feiyue Enviromental Technology Co., Ltd is located in
Shijizahuang City, built at 2013,
professional manufacturer in the field of RO pure/mineral water
treatment equipment, waste water /
swimming pool water treatment equipment, bucket or bottle filling
machine, wholesale agent of branded
RO Membrane, membrane housing, control valve, PP sediment filter,
Ozone generator and all kinds of
accessories for water treatment equipment.
1. Own factory and engineers have experience over 20 years.
2. Own patent in RO Pure/Mineral water treatment equipment.
3. OEM & ODM available.
4. Direct manufacturer can offer the best price.
5. Already obtained worldwide partners.
6. Supply project plan, field installation, training engineer for
client free of charge.
7. Products have 1 year guarantee period.
8. Lifetime after services for all our products.
Welcome to contact us.
Shijiazhuang Feiyue Environmental Technology Co.,Ltd